Silvercroft to D&H Air Conditioning & Heating, 3990 S Evans Blvd Tucson, AZ 85714
Today, we were in the Rancho Agua Dulce area (code: 7XM3+2C), West of Tucson, on the other side of I-10. We performed a full inspection of a Rheem gas package unit. D&H inspects and repairs any air conditioning unit. We checked the thermostat, the filter, the voltage, the amp draw, the safety switches, all the electrical connections and wiring, the coils, the blower wheel, the motor, the flush drain, the current controllers, the unit starter, the temperature split, all pressures, the compressor amp and the condenser fan amp. We also washed the condenser coil. The Rheem unit is working at this time but we noticed the evaporative coil had rusted with some corrosion: we recommended coil guard to protect the unit from future rust and corrosion. To be noted too: the current controller reading is out-of-specs on the compressor side (68.5/70), so we recommended replacing the current controller. The condenser fan motor was over-amping 2.1/2.0, so we recommended replacing the condenser fan motor, due to age. D&H Air Conditioning’s inspections are known to be thorough and meticulous. If you really want to know about the state of your own A/C unit, call our hotline to schedule an inspection/check-up by one of our NATE-Certified technicians. Call [phone] or click on the button below if you are on mobile. Thank you!